TD Compact Four Pole Distribution Block, 40 A
Thanks for your submission. A customer service agent will be in touch soon to help you further.
Application images Resources3D models
|Design Guideline for Distribution Blocks, Power Blocks and Power Terminals|
|Derating according to Ambient* Temperature (°C) to maintain working temperature of 85°C|
|Ambient Temperature (°C)||30°||35°||40°||45°||50°||55°||60°||65°||70°||75°|
|Derating Coefficient (d)||1||1||1||0.94||0.88||0.82||0.75||0.67||0.58||0.47|
|*environment around the terminal blocks inside the enclosure|
- nVent products shall be installed and used only as indicated in nVent's product instruction sheets and training materials. Instruction sheets are available at www.nvent.com and from your nVent customer service representative. Improper installation, misuse, misapplication or other failure to completely follow nVent's instructions and warnings may cause product malfunction, property damage, serious bodily injury and death and/or void your warranty.